GAS REGULATOR SEAT TEMPERATURE DURING GAS TURBINE START-UP
Pressure regulators are to be employed at a gas-fired power station to reduce upstream gas pressures from a maximum of 15 MPa to approximately 3.5 MPa. Due to the Joule-Thompson effect, the resulting gas temperature drops could be in the region of 55°C. The dew-point temperature of the hydrocarbons (gas) flowing through is -15°C and the minimum ambient temperature of the area is -6°C. Thus the regulators could potentially be subjected to gas at -61°C at start-up. According to the valve manufacturer, temperatures as low as -20°C can be tolerated for some time, provided that condensation does not occur.
More Case Studies
You might also be interested in these CASE STUDIES
Faulty systems operation results in significant power generation losses. The purpose of this case study is to communicate a case where…